This part of ISO 10816 gives instructions for the evaluation of vibration on rotodynamic pumps for industrial applications with nominal power above 1 kW. It defines the special requirements for evaluation of vibration when the vibration measurements are made on non-rotating parts (bearing housing vibration). It provides specific guidance for assessing the severity of vibration measured on bearing housings of rotodynamic pumps in situ and for the acceptance test at the manufacturer's test facility or in the plant. This part of ISO 10816 also gives general information and guidelines for assessing relative shaft vibration of the rotating shaft. This part of ISO 10816 specifies zones and limits for the vibration of horizontal and vertical pumps irrespective of their support flexibility.
Part 14: Mechanical vibration of certain machines with shaft heights 56 mm and higher – Measurement, evaluation and limits of vibration severity 1 Scope This. Part 114: Vibration measurement and limits Originated as AS 13. 10816 Mechanical vibration—Evaluation of machine vibration by measurement on.
The general evaluation criteria are valid for operational monitoring of rotodynamic pumps and for acceptance tests 1) in situ or at the manufacturer's test facility if specified. For the acceptance test at the manufacturer's test facility, special conditions are given. For monitoring the vibration values during long-term operation, two criteria are provided for assessing the machine vibration.
One criterion considers the magnitude of the observed vibration and the second considers changes in magnitude. The evaluation criteria are applicable for the vibration produced by the pump itself and not for vibration which is transmitted to the pump from external sources. The criteria mainly serve to ensure a reliable, safe long-term operation of the pump, simultaneously minimizing harmful effects on connected devices. Additionally, recommendations are given for defining operational limits and setting alarm and trip values. For pump units with integrated electrical motors (impeller directly on the motor shaft or impeller shaft rigidly connected to the motor shaft), this part of ISO 10816 applies to the whole coupled unit.
For flexibly coupled motors, this part of ISO 10816 is applicable for the pump only. Also, separately mounted drivers are not within the scope of this part of ISO 10816.
Those drivers are dealt with in ISO 10816-3. The following types of pumps are excluded from this part of ISO 10816: — reciprocating and rotating positive displacement pumps; — reciprocating engine driven pumps; — pumps in hydraulic power generating and pumping plants with power above 1 MW (see ISO 7919-5  and ISO 10816-5); — solids handling, slurry and submersible pumps. Torsional vibration is not dealt with in this part of ISO 10816. Cambridge Soundworks 88cd Service Manual: Full Version Software. 1) Wherever acceptance tests are mentioned in this part of ISO 10816 it should be taken into account that all the details about place, size and form of those test procedures are optional and need to be specified and agreed between both parties of a contract.
Comments are closed.